Revise the International Fire Code: Chapter 20: - Specifically include "printing inks" in the definition of "organic coating." - Define equipment specifically discussed in the standard, such as open and closed kettles. - Require heated tanks and vessels containing flammable and combustible liquids to have equipment to prevent overheating, such as: devices to stop the heating process if the temperature exceeds the safe operating limits; devices to stop the heating process if the flammable vapor control equipment malfunctions (e.g., building ventilation system or heated tank vent); and a heating medium that is unable to heat the tank above safe operating temperatures. Chapters 20, 27, and 34: -Define "open", "closed", and "sealed and vented" process tanks. -Define "non-listed" process tanks. -Prohibit heating flammable and combustible liquids above their flashpoints in tanks inside buildings unless the tanks are sealed and vented to the building exterior.